Installation Instructions for Stainless Steel Solenoid Valve
Stainless Steel Solenoid Valve Installation Instructions 1. When installing, the solenoid valve coil should be upward and keep the vertical position. The arrow or mark on the solenoid valve should be consistent with the flow direction of the pipeline. It should not be installed in a place with splashing or water leakage. 2. The working medium of the solenoid valve should be clean and free of particulate impurities. The dirt and filter on the surface of the solenoid valve's internal parts must be cleaned regularly. 3. Installation instructions for the stainless steel solenoid valve when the solenoid valve fails 1. When installing the solenoid valve coil upwards, and keep the vertical position, the arrow or mark on the solenoid valve should be consistent with the flow direction of the pipeline, and must not be installed in a place with splashing or leaking water. 2. The working medium of the solenoid valve should be clean and free of particulate impurities. The dirt and filter on the surface of the solenoid valve's internal parts must be cleaned regularly. 3. When the solenoid valve fails, in order to isolate the solenoid valve in time and ensure the normal operation of the system, it is best to install a bypass device (see Figure 1). Note: The valve on the bypass must be closed at ordinary times. If the solenoid valve is installed on the bracket, the diameter of the solenoid valve should be smaller than that of the valve on the main pipeline. As shown in figure (two). 4. Before installing the solenoid valve, the pipeline must be cleaned. It is recommended to install a filter in front of the valve and install a trap in the steam pipeline. 5. Do not install the valve in the low recess of the pipeline, so as not to hinder the action due to the precipitation of steam, condensate, impurities, etc. 6. The normal type cannot be used in explosive hazardous situations. 7. In the case of insufficient pipe rigidity, it is recommended to fix the pipes before and after the valve with brackets to prevent vibration caused by the solenoid valve when it is working. 8. Before installation, pay attention to read the product label, carefully read the instruction manual, and judge whether the product meets the conditions of use. 9. Pressure gauges should be installed on the pipes before and after the solenoid valve to observe the pipe pressure.
- E-mail: firstname.lastname@example.org - Wechat : +86 13821000231
- Whatsapp: +86 13821000231
- Factory address: No.12 outer ring industry park zhong bei industry park (northern area), xiqing district,tianjin.